210.8(E) Crawl Space Lighting Outlets. GFCI protection shall be provided for lighting outlets not exceeding 120 volts installed in crawl spaces.
Comment: GFCI protection for lighting outlets not exceeding 120 volts is now required where lighting outlets are located in crawl spaces, at or below grade level, of dwelling units or non-dwelling units. At least one lighting outlet containing a switch or controlled by a wall switch shall be installed where a crawl space is used for storage or it contains equipment requiring servicing. (210.70(C))